|Place of Origin:||Zhejiang, China (Mainland)|
|Minimum Order Quantity:||1 piece|
|Packaging Details:||Carton packing|
|Delivery Time:||7 day|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||10,000 / month|
|Product Name:||Control Signal Surge Protector||UC:||24V AC|
|Warranty:||2Year||Certificate:||CE TUV IOS9001|
TRSS-485 control signal surge protection device
Color: white / red
The control signal lightning arrester is used for lightning protection of the data communication system, and can protect four signal lines or two pairs of twisted pair information lines, providing high-energy coarse-level protection and low-energy fine protection for the data lines, and also being 1, 2 and 3 respectively. 4 pairs of lines provide fine differential mode protection and common mode protection to ground, thus effectively absorbing and transferring energy shocks caused by lightning strikes and surges, and introducing energy into the earth through grounding cables, ultimately protecting sensitive electronic equipment from damage.
The control signal surge protector is connected in series with the front end of the protected device. When the transmission line is subjected to induced lightning and other transient overvoltage surges, the inrush current is discharged to the earth through the protection branch of the surge protector, and the output is output. The voltage is clamped to the voltage range allowed by the device, thus ensuring the safety of the operating equipment.
|Main technical parameters||TRS-485|
|Max continuous operating voltage Uc(VAC)||24|
|Voltage protection level Up(V)≤||40|
|Max discharge current (8/20μS) lmax(kA)||10|
|Nominal discharge current (8/20μS) ln(kA)||5|
|Response time ns||<1ns|
|Degree of protection||IP20|
|Application||Primary protection for in line|
|Remarks||Other Uc can be customized|
1.The signal lightning arrester can be installed in the LPZ0-1 area or directly connected in series to the front end of the protected equipment (or system). The closer it is to the protected equipment (or system), the better.
2. The grounding of the lightning arrester is connected with the shortest possible line. The protector is grounded by terminal grounding, and the grounding wire must be connected to the lightning protection ground wire (or the outer casing of the protected equipment). The shielded wire of the signal can be directly connected to the ground terminal.
3. Connect the lightning protection device (SPD) between the line and the device port to be protected. Connect the grounding port on the SPD to the ground net with multiple strands of copper wire, and ensure that the grounding resistance is not more than 4 ohms.
Incorporated in 2006, Zhejiang Thor Electric Co., Ltd has built everything to offer a wide range of innovative and reliable surge protection solutions and products. It is our goal and mission to connect our customer challenges with high-quality, right-priced solutions and products – completed by unrivaled customer service and technical support.
Contact Person: William